Ballybougal 200mm PE Rising Main & 2 Pump Pumping Station
Clients Consulting Engineers: Waterman Moylan
Martin Hannan: 087 7971048
Brief Summary Works:
Design, Construction and Commissioning of 2.5km of 200mm PE Rising Main & Two Pump Pumping Station in Ballybougal Village.
Specialist M&E Subcontractor: EMR Integrated Solutions
Pump Station Design 2D Tanks, with Dual Pumps, capacity 30,000 litres. Design included allowance of capacity of sump to be equivalent to 24hrs of DWF. This was calculated by clarifications from Fingal CC of their p.e flow rate and the persons per property.
The control panel was housed in a control building which was approximately 2m from the pump sump access. All works regarding electrical cables running between the pump sump and the control building was also designed and constructed by RCCS Ltd.
The Pump Specification was a starting current 28A. each at a flow rate of 3 to 11 LPS at a head of 10mwg.
Supply, install and commission 1no. Main Control Panel containing 2no. 3KW Schneider Ethernet variable speed drives, Auto/Manual select, Low flow cut-out, Sump level control, Duty/Standby/Assist. I No. PLC.
Supply and commission 2 no Flygt 3085 SH 3~ 255 Submersible Sewage Pumps c/w Duckfoot, guiderails, lifting chains, pump stands and isolating valves.
1 no. 100mm Siemens Mag5000 Electromagnetic Flowmeter c/w 20m of cable.
1 no. Hydroranger Ultrasonic flowmeter and remote sensor for sump level control and indication.
Signal marshalling for Fingal CC as per there requirments
1 no. 1200x1200x400mm Weatherproof Kiosk to house the above, c/w 3~ consumer units, isolators, light and heater.
1 no. ESB Mini-pillar.